9 Dec Part AC metal-enclosed switchgear and controlgear for rated to IEC – the new standard for medium-voltage switchgear. All new medium-voltage switchgear assemblies installed after February 2, must fulfill the new standard IEC/EN 13 Sep IS/IEC High-Voltage Switchgear and Controlgear, Part AC Metal -Enclosed Switchgear and Controlgear for Rated Voltages.
|Country:||Bosnia & Herzegovina|
|Published (Last):||2 December 2006|
|PDF File Size:||9.18 Mb|
|ePub File Size:||4.81 Mb|
|Price:||Free* [*Free Regsitration Required]|
IEC – HV Switchgear And Controlgear
Are there any published industry codes or standards that cover the inventory tracking, decommissioning, storage, chain of custody, disassembly, and disposal of the waste materials, etc. Hi, For Auto Reclosures which we plan to install for a 50 Hz system is it ok to accept the type test reports done in a 60 Hz laboratory??? The content is copyrighted to EEP and may not be reproduced on other websites. However, both technologies — the vacuum arc-quenching principle and gas insulation — were not adequately taken into account in the existing standard.
According to IECtwo disruptive iec 62271 part 200 were iec 62271 part 200 in a series of 15 voltage impulses for the test with rated lightning impulse withstand voltage.
Leave a Comment Click here to cancel reply. In order to guarantee safe access to the individual switchgear components, e. Facebook Iec 62271 part 200 Google Plus Twitter. According to the new standard, the series must be extended by another fi ve voltage impulses iec 62271 part 200 a disruptive discharge has occurred during the fi rst 15 impulses.
Although the old IEC standard was very helpful, in time it was superseded by the technological progress.
Peak and short-time withstand current tests to verify the dynamic and thermal current carrying capacity of the main and earth circuits; the tests are performed with rated peak short-circuit current or rated iec 62271 part 200 making current or rated shorttime current or rated short-circuit breaking current.
The same iec 62271 part 200 to IEC — the new standard for medium-voltage switchgear. Correspondingly important is their reliable functioning, a clearly defined switching behavior according to specified parameters as well as the protection of personnel and protection against operational interruptions when an overload occurs. Significantly stricter changes have also been implemented here. Ic Auto Reclosures which we plan to install for a 50 Hz system is it ok to accept the type test reports done in a 60 Hz laboratory???
IEC | IEC Webstore
For this reason, the test duties Ts and Iec 62271 part 200 from the IEC standard iec 62271 part 200 stipulated for the test of the circuitbreaker inside the switchgear panel.
AC metal-enclosed switchgear and controlgear for rated voltages above 1 kV and up to and including 52 kV. High-voltage switchgear and controlgear Part Degree of protection tests 662271 verify the protection against electric shock and foreign objects. With a cubicletype design, the incoming cable had to be isolated, but the busbar itself could remain in operation.
Pressure and strength tests to verify the gas tightness and pressure resistance for gas-fi lled switchgear.
The switching capacity may get a negative infl uence from the different arrangement of the switchgear with contact arms, moving contacts, conductor bars, etc.
In addition, the five following new criteria must always be completely fulfilled no exceptions iec 62271 part 200 permitted:.
Temperature rise tests to verify the current carrying capacity with rated normal currents. Therefore, with switchgear in metalclad or compartmented design, the busbar in the busbar compartment and the incoming cable in the connection compartment could remain in operation. Therefore, at the end of the nineties, the responsible IEC committees decided iec 62271 part 200 the reformulation of the switchgear standard, which finally came into effect as Iec 62271 part 200 in November The International Electrotechnical Commission IEC has taken up the task of developing the required specifications, their worldwide standardization and further development.
Instead, it is now mandatory to carry out the test in the corresponding switchgear panel. This resulted in the first-time use of gas insulation with the important features of climatic independence, compactness and maintenance-free design.
Fit for IEC 62271-200?
There is also the possibility of voluntarily certifying switchgear for resistance to internal arc faults and for personal protection. Switchgears are important nodal points in modern iex distribution. IEC — for four decades this abbreviation was the decisive factor for the type testing of metal-enclosed switchgear.
Nadun Galloluwe Jan 29, In the iec 62271 part 200 there are tens of thousands of switchgear panels of the primary and secondary distribution iec 62271 part 200 based on this standard in use — certified according to the mandatory part of the standard and, if required, according to optional tests.
The vacuum arc-quenching principle is technologically so superior to other arc-quenching principles that the circuit-breaker can be fixed-mounted again.